The industry has revolved with many products for the cooling coil control valves. The goal is to get good delta T and save energy. What is the most cost effective option? Majority of district energy system get lower delta T during low loads compared to peak load. Coils are oversized so why not higher delta T for low Also chilled water is not for cooling. It is for dehumidification. How to optimize AHU unit controls?
Session Track 1C
Hemant Mehta, WM Group
1800 West Park Drive, Suite 350
Westborough, MA 01581 USA
Phone +1 (508) 366-9339
Fax +1 (508) 366-0019
© 2019 International District Energy Association, All Rights Reserved. Site by eConverse Media