Gardens -03 DCP is designed and built for 15,000 TR. Chillers had dedicated primary pumps for flow rate equivalent to 12.8°F; existing plant operational delta T is 9.3°F. Empower replaced existing constant speed primary pumps with variable flow Primary pumps corresponding to the actual Delta T. Pumps were selected for 2.4GPM/TR, replacing 1.875 GPM/TR pumps. The key aspects of up gradation are effective utilization of plant capacity, mitigating Low Delta T syndrome and other financial benefits.
Session Track 1D
Tariq Al Yasi, Empower Energy Solutions
1800 West Park Drive, Suite 350
Westborough, MA 01581 USA
Phone +1 (508) 366-9339
Fax +1 (508) 366-0019
© 2019 International District Energy Association, All Rights Reserved. Site by eConverse Media